Product is the same with place which electro-area, such asliving area, emporia, industy, site of build, oil field,roadway, port airport and temporary electro-area of build and so on.
•Small bulk, perfect figuration. Convenience to fix, operate, upkeep, and credibilityto run.
•Three-phase five-column structure transformer winding connection group using Dyn11 connection with low loss, low noise, zero-sequence voltage from suppression, interfering phase voltage, lightning protection performance, the characteristics of unbalanced load capacity.
•We adopt back-up protective fuse and inserted fuse to protect it.
•Made crust of armor plate, and deal with especially technics to antisepsis.
•Crust protection grade is IP33.
National standards of product
GB1094.1-1996 ( power transfarmer part one general principle )
BGAT6451-1999 (the technical parameters and requirements of therr-phase vacuum-impregnated power
GB/T16274-1996 ( the technical parameters and requirements of vacuum-impregnated poweer
BG3906-1991 ( 3~35kV AC Metal Enclosed Switchgears )
GB7251-1997 (low voltage complete switchgears and control equipment)
GB/T14048-1998 (general principle of low voltage switch equipment and control equipment)
GB/T17467-1998 ( high/Low voltage package substaion )
GB/T11022-1999 (common technical requirement of high voltage switchgears and control equipment standard )
Product use condition
Altitude Above Sea Level: ≤1000m
Highest Average menmal Temperature +35°C
Maximum Difference in Daliy Temperature 25K
Rilative Humidity of Daily ≤95%
Rilative Humidity of Daily ≤90%
Earthquake Intensity: 8 degree
Defilement level: III